Cleanzine: your weekly cleaning and hygiene industry newsletter 16th March 2023 Issue no. 1056
Your industry news - first
The original and best - for over 20 years!
We strongly recommend viewing Cleanzine full size in your web browser. Click our masthead above to visit our website version.
Interserve Facilities Management fined for safety failings
Interserve Facilities Management has been fined after multiple safety failings at a laboratory site for the Animal Health & Veterinary Laboratories Agency in Weybridge.
Hove Crown Court heard how, in September 2014, mains power was lost at the site which includes high containment laboratory facilities required to safely handle high hazard pathogens that are a serious risk to human health and the environment.
The FM company was contracted to the site and was responsible for delivery of maintenance activities for many of the mechanical and electrical systems required for containment and control of high hazard biological agents in microbiological containment laboratories.
The Court heard that when mains power was lost, of the 12 generators in place to supply emergency power to the site, two failed to operate and two started but subsequently failed in operation, one of which also caught fire.
The emergency escalation system was triggered, and the Fire & Rescue Service attended the site. Power was fully restored later that day.
As a result of the emergency generator failures, the Court was told all power was lost to a number of high containment facilities for several hours, affecting the site's safety systems.
An investigation by the Health & Safety Executive found a number of failings of the contractor in relation to the maintenance activities undertaken on standby generators that could have resulted in employees being exposed to a risk of harm from biological agents.
Interserve (Facilities Management) of Capitol Tower, Waterloo Road, London, pleaded guilty to breaching section 3(1) of the Health & Safety at Work etc. Act 1974 and have been fined £93,600 and ordered to pay £32,056 costs.
Speaking after the hearing, HSE intervention programme manager and lead investigator in the case, Dr Keith Stephenson said: "Interserve Facilities Management failed to effectively maintain the standby generators that were a key emergency control measure needed to work safely.
"Fortunately, the consequences of the multiple generator failures were significantly reduced by the timing of the incident, both in terms of the day of the week and the laboratory studies being undertaken at that time.
"Had the incident happened on a different day or when different studies were being undertaken, staff and the nearby environment could have been exposed to high hazard biological agents with serious consequences."
15th November 2018